fire alarm work for permit #2 on the "tower tour" remodel on floor 1; addition is 1 speaker/strobe that is being installed due to a new wall. fire alarm permit #1 for this remodel was done under pa 2017-1115-4001 and 2017-0728-3173. maher na
8th floor - conversion of office space, which was originally guest rooms back to guest rooms. no additional quantity of rooms being added. mep & life safety separate permit. n/a maher ordinance. work in rooms 831, 832, 8/f, tower 3
ground fl: interior retail ti including one (n) restroom. new non-bearing partitions, lighting, electrical distribution. mechanical, electrical, life safety and fire sprinkler to be design/built under seperate permits. maher na
barrier removal. general renovation of existing parking level and accessibility upgrade along the path of travel. work inclues accessible parking spot restriping to bring up to cook. work tower 111 on floor 1, 6, 7,8, 9, 10, 11
fire alarm work for the "main lobby" remodel on floor 1; additions are 2 speaker/strobes, as well as the relocation of 2 smoke detectors, 1 speaker, 5 speaker/strobes and 4 strobes. ref pa 201603031149. n/a for maher.
renovation to (e) women's & men's locker rooms to include demo of lockers, lavatories, urinals, toilet stalls & showers. all items to be renovated to comply with current code & provide (n) finishes. n/a ordinance #155-13
1st fl: fire alarm work to revise the detector layout for the 'main lobby' remodel project. the changes result in the addition of 1 smoke detector & the removal of a retractable door closure. ref pa #2015-0924-7980. n/a maher ordinance
proposal to install verizon wireless: das system, including 2 new equipment racks, 1 equipment cabinet, and 6 wall -mounted radios. all within extg head end room. no antennas are proposed. no exterior work is proposed. n/a maher.
renovation of (e) ground fl lobby to include (n) bar w/ lounge seating & nearby dining areas. alterations to include (n) finishes, lighting, furniture, millwork & food service equipment. scope also includes upgrades to (e) interior ramp to become fully accessible. l/s and sprinklers under sep.permit
project is the limited scope up-fit of an (e) single level tenant space "travel traders" new work is to include but not to be limited to the wall finishes, flooring, fixtures, lighting & equipment. n/a maher ordinance
25th to 28th floor: fire alarm work for the ada room upgrade. t.i. project on floors 25,26,27,and 28. the additions are 8 smoke detectors, 7 modules and 15 strobes. ref. appl. #2013.0821.4878. mahner n/a.
elevator - remove all fire sprinklers in elevator machine room & the top of the hoistways in tower 2. sprinkler heads in pits to be lowered below 24", elev to comply with preapp (apply 10/10/14 attacged) & 2013 sbc sect 3006.4.1.
addition of 3 smoke detectors and 16 strobes for the phase 1 ada room upgrades project various floors. ref 201308214878. work in 19 rooms between floors 29 and 42. all need to be tested. compliance with maher ordinance # 155-13 does not apply
level b2: addition of 1 relay module for the kitcen elevator modernization to flash firefighter's hat light on elevator mach room and elevator hoistway smoke dtector activation. project on level b2. the module connects onto the fire alarm system.
renovation of 566 guest rooms in tower 1 on floors 7 - 44. this is inclusive of (n) plumbing fixtures at (e) locations. all new finishes & (n) light fixtures with equal wattage (or less) at (e) locations. mechanical system to remain.
document harddship for ballroom level (3rd fl) men's restroom stall revision. document scope of work ada accessibility guidelines using 1991 cbc as the reference guidelines. reference pa# 201107120009.
floors 4 & 6 - 'as-built' permit (per the sffd) for fire alarm system work done under original application #2012.03.16.6183. the revisions resulted in the deletion of 4 smoke detectors, & the additoins of 1 relay module & 1 strobe.
addition of 3 "loop" modules, 96 smoke detectors, 45 relay modules, 36 speaker/strobes, and 16 door holders for the "meeting room". upgrade porject on floor 4 and 6, smoke detectors provide "full coverage" for rooms and common corridors with associated fire/smoke dampers.
continental ballroom level - addition of 16 smoke detectors, 34 speaker/strobes, 10 speakers, 2 relay modules, 12 door holders, & 1 strobe power supply for the "continental ballroom" remodel project. 6 speaker/strobes are also being relcoated. all devices connnect onto the fire alarm system.
interior non struc remodel of 498guest rooms in tower #3. remodfel bathrooms and interior finishes. new unit entry door on all 550 rooms in tower#3. all existing mechanical system to remain. all restroom lighting shall be high-efficacy or occupancy sensor control per cec 150(k). verify door listing
occupant load calcs only of continental ballroom (level 2).ref pa# 2007/06/08/3444. for occ. load verification only. req for public assemb. permit. fire insp to field verify exit signage; horiz exit standpipe locations; panic hardware at all required door locations; & occ load signage as per
mechanical replacement of supply & return fan motors, hot water coils, chilled water coils, control dampers, electrical disconnect reconnect, reinstall smoke duct detectors, air & water balance to original design (location @ 12th. flr. penthouse).
interior tenant improvement to (e) plaza. scope of work to inclcude new finishes, lighting and electrical work. (e) mech. system to remain as is. groundfloor only. remove & cap (e) fire hose cabinet. fire sprinkler in separate permit.
fabricate and install 1 new triangle style awning with graphics. 6'x4' projection and 9' drop to include a 9" fixed valance, glazed steel tube primed and painted. fabricate cover of awning canvas fasten with teck screws.
revision to life safety permit appl.# 2007.11.20.8597 on lobby and 2nd fl (within lobby area). add 21 smoke detectors, 1 duct detector, 2 relay modules for fire code coverage at magnetic door holders and fire/smoke dampers associated with 2-hour wall construction.
demolition of existing non bearing walls ceilings, ducting, electrical and floor coverings on the first floor of tower three. demolition is to be referenced to application #2007/0608/3444. sprinkler and life safety to remain. no structureal work under this permit. no exterior work under this permit.
interior demolition of existing cafe, lobby, and retail spaces including walls, ceilings, flooring. wor on 1st floor, tower 3 demo under 200706083444. spaces at demo areas to remain vacant until ti permit
all interior work,no exterior alterations.remodel bathrooms,convert some bathtubs to showers,new lighting & switches,install new toilets in (e)locations.new bathroom doors.remove select connecting doors,furrout wall in some location.no ada renovations bldg.is in compliance.